Methodology of the Primary Data Reconstruction of Single Pipe Heating Systems/Vienvamzdžių šildymo sistemų pirminių duomenų nustatymo metodika
|Published in:||Journal of Civil Engineering and Management, October 1999, n. 5, v. 5|
The majority of dwellings in Lithuania are situated in blocks of flats. The dwellings were built after World War II and they are heated by single pipe central heating systems, connected to district heating. The dwellers are not quite satisfied with such a heating system and try to improve it, but do that in a wrong way, by increasing the surface of radiators. Such means lead to violation of thermal regime and comfort conditions for other dwellers. There exists sometimes the necessity of reconstructing premises and together—the heating system. During the reconstruction the primary heat fluxes from radiators should be known, but very often such data are lost and only the size of radiators (number of sections) are known. To reconstruct the required primary data for single pipe systems is complicated because the temperatures of inlet and outlet water for radiators are unknown. In this article the methodology is proposed how to perform the calculations leading to the required data. The aim of calculations is the establishment of heat fluxes from each radiator connected to the riser. Heat flux from radiator can be calculated according the formula (1) but the complex coefficient is unknown. It could be found from formulae (2) but some magnitudes are unknown. According to the proposed methodology the values of unknown magnitudes are taken approximately and calculations are performed with iterations. In such a way the flow rate of water in riser is established from formula (3), which is the same for each radiator (the property of single pipe system). From formulas (3) and (4) an equation is produced (5), and is used for calculations of unknown temperatures. The equation (6) is used for calculation of heat fluxes from radiators. To carry out the above-mentioned calculations without computer practically is impossible due to many cycles of iteration. The programme was prepared to make easy all these calculations. The scheme of algorithm of programme is given in Fig 1. An example of calculation is given in this article. Calculations were fulfilled by newly created programme. The riser chosen for calculation is shown in Fig 2. The results of calculation are given in Table 1. The table shows that according to the proposed methodology the programme based on it can be used for reconstruction of primary data of single pipe heating systems successfully.
|Copyright:||© 1999 The Author(s). Published by VGTU Press.|
This creative work has been published under the Creative Commons Attribution 4.0 International (CC-BY 4.0) license which allows copying, and redistribution as well as adaptation of the original work provided appropriate credit is given to the original author and the conditions of the license are met.
- About this
- Published on:
- Last updated on: